8:55 AM, 1st March 2018, About 4 years ago 12
We bought a house as an investment rental property in January 2016. A new boiler had been fitted in December 2015 so we were fairly confident that we would not be incurring expense on the boiler for a few years. We had used an agent for various activities on the marketing and letting process and their service had been good so we decided to use them for the gas safety check and boiler service which they carried out in Dec. 2016 and Dec.2017.
On Saturday the boiler failed completely the main heat exchanger badly corroded together with the secondary heat exchanger . The plumber confirmed that the filling loop had been installed incorrectly so mains water had been entering the whole system for 2 years . Other installation errors were also apparent albeit they would not have caused the boiler to fail.
He removed the magnetic plug and said it was full of debris from corrosion and probably because the system had probably not been power flushed on installation. It was the worst he had seen in 21 years .We now face a bill of £3451 to replace the boiler and rectify the faults. The boiler manufacturer’s engineer came out a year ago to change a faulty gas valve. So 2 services and a manufacturers engineer attend to the boiler and none of them check the magnetic plug or spot that the filling loop is incorrectly installed . Am I missing something here ?
The agent’s response is that it assigned 2 different engineers for the services ( which in my opinion makes their standard of service even worse ) and that it would be useful to have more clarity around boiler services .
Can Property 118 not develop a quality service and resource it to stop this sort of thing happening ?
Which conducted a survey recently and confirmed 40% of boiler services are inadequate and miss basic but in some cases critical items.
Rant over but any suggestions would be gratefully appreciated.
And yes I am writing to the boiler manufacturer next.
Please Log-In OR Become a member to reply to comments or subscribe to new comment notifications.
Previous ArticleWelsh Housing Condition Survey 2017-18
|“Account”||means an account required to access and/or use certain areas and features of Our Site;|
|“Cookie”||means a small text file placed on your computer or device by Our Site when you visit certain parts of Our Site and/or when you use certain features of Our Site. Details of the Cookies used by Our Site are set out in section 13, below;|
|“Cookie Law”||means the relevant parts of the Privacy and Electronic Communications (EC Directive) Regulations 2003;|
|“personal data”||means any and all data that relates to an identifiable person who can be directly or indirectly identified from that data. In this case, it means personal data that you give to Us via Our Site. This definition shall, where applicable, incorporate the definitions provided in the EU Regulation 2016/679 – the General Data Protection Regulation (“GDPR”); and|
|“We/Us/Our”||Means Property118 Ltd , a limited company registered in England under company number 10295964, whose registered address is 1st Floor, Woburn House, 84 St Benedicts Street, Norwich, NR2 4AB.|
|Name of Cookie||Purpose||Strictly Necessary|
|JSESSIONID||Used only to collect performance data, with any identifiable data obfuscated||No|
|__cfduid||This cookie is strictly necessary for Cloudflare's security features and cannot be turned off.||Yes|
|Name of Cookie||First / Third Party||Provider||Purpose|
|__utma, __utmb, __utmc, __utmt, __utmz||First||Helps to understand how their visitors engage with our website|
|_fbp||First||Helps to understand how their visitors engage with our website|