13:03 PM, 8th April 2013, About 8 years ago 2
Just before the 1st annual check on a newly installed combi boiler my tenant reported a smell of gas when she showered.
At first we thought it was incomplete combustion and a leaky flue, which is exposed in the bathroom ceiling. On opening up, the inlet duct was not fully on the gas valve seating. But the leak persisted.
After a lot of probing both combi, pipework and gas -stove we tracked another leak down to what appears to be the test nipple in the gas-valve, a negligible leak with the heating turned off. Very small leakage on heating only, but out with whoosh when the shower turned on [sensor blips almost continuous]. Failure certificate issued and boiler turned off and isolated. Hob left for use – but the tenant didn’t touch it all weekend. emergency electric radiators deployed – but she didn’t ask for the emergency electric rings.
So we booked a manufacturers inspection. No reply at 7pm Friday, so rang at 9am Saturday, as advised, and got through after 40mins listening to the same message!
Engineer called about 8.30 to advise attendance after 10am. Arrived about 10.15am. Different sensor and no leak found. Carried out latest mods to the fully exposed flue and left. No clearance certificate issued. The only 2 differences between today and Friday – East wind has dropped [flue exits near the bottom of a 4 storye east facing wall] and the unit was cold on start-up.
I have two others installed this year which I feel I must inspect next week.
The interesting thing as the leak would not be found during a normal certification check as the RGI checks for pressure drop with the machine off! perhaps a change is required. More thorough with gas fires, I feel.
Manufacturers name withheld for the usual reasons.
Please Log-In OR Become a member to reply to comments or subscribe to new comment notifications.
Advice and implementation provided by a practising Barrister-At-Law with £10,000,000 of Professional Indemnity InsuranceBook Now
Previous ArticleNo pet policy, tenants have 2 dogs with pups, help!
Next ArticleRepossession Property in County Durham
|“Account”||means an account required to access and/or use certain areas and features of Our Site;|
|“Cookie”||means a small text file placed on your computer or device by Our Site when you visit certain parts of Our Site and/or when you use certain features of Our Site. Details of the Cookies used by Our Site are set out in section 13, below;|
|“Cookie Law”||means the relevant parts of the Privacy and Electronic Communications (EC Directive) Regulations 2003;|
|“personal data”||means any and all data that relates to an identifiable person who can be directly or indirectly identified from that data. In this case, it means personal data that you give to Us via Our Site. This definition shall, where applicable, incorporate the definitions provided in the EU Regulation 2016/679 – the General Data Protection Regulation (“GDPR”); and|
|“We/Us/Our”||Means Property118 Ltd , a limited company registered in England under company number 10295964, whose registered address is 1st Floor, Woburn House, 84 St Benedicts Street, Norwich, NR2 4AB.|
|Name of Cookie||Purpose||Strictly Necessary|
|JSESSIONID||Used only to collect performance data, with any identifiable data obfuscated||No|
|__cfduid||This cookie is strictly necessary for Cloudflare's security features and cannot be turned off.||Yes|
|Name of Cookie||First / Third Party||Provider||Purpose|
|__utma, __utmb, __utmc, __utmt, __utmz||First||Helps to understand how their visitors engage with our website|
|_fbp||First||Helps to understand how their visitors engage with our website|